I have a Bad Pressure switch on this Rheem Furnace. It is a RGED model. It has a double (PS) One from the intake and one at the exhaust. I have a adjustable (PS) and need to know the following. Will a Clevland adjust 1-4 work safely with this furnace set at the RHEEM setting of 1.65 WC.
The reason I need to know for those who will ask. I have been waiting for Rheem to send me a replacment for 2.5 weeks and now I'm told it will be 2-3 more weeks for the part. Its a long time to not have heat in JAN & FEB in TN
Thank you for any who can help a spec sheet for this unit would be GREAT. Cause rheem wont help us ASdealers.