Results 1 to 2 of 2
02-03-2005, 08:17 PM #1Regular Guest
- Join Date
- Feb 2005
I have a tracer summit system monitoring nine Voyager/Precedent RTU's with Retiatel. On one of the units the active setpoints in summit switch on their own to 90heating and 90cooling,after a cycle of power (of the unit) they revert to their controlling setpt.All of the boards in the RTU have been switched with a known good unit and the problem didn't follow.
Any ideas ?
02-03-2005, 10:06 PM #2
You need to look at the sticker on the reliatel board in the rtu, it should read rev 3.0 or 3.1 for a heat pump or higher. If not replace the board, Trane should warranty it under a recall program this is a common problem with summit and programable zsm's and lower revision boards.