Definitely need a temp. reading to know whats going on.On that model (1978-1980) the blower should come on in 75 seconds with +/-20% variance (per specs.) from the time of the call for heat.Flue damper was an accessory item. Also that model has a fuseable link in it too. Bad board, bad limit switch, or a hot mama?