Goodman furnace GMV8 2 stage, variable speed.
I had this furnace installed on the month of September 2004.
The problem I have is that the induced-draft blower assembly is very noisy.
Actually you can hear the noise from the 1st floor (living room) of my house.
Also the vibration generated by the induced-draft blower assembly propagates into the flex duct making the noise impossible to stand if you are near to the furnace (3-5 ft away)
I called the company that installed it and they said that this is normal with 80% furnace.
Also I called Goodman CSR and they told me that the furnace is not noise tested.
Anyone had same experience or knows what the problem is?
Thanks a lot,