Liebert Model CM60AF-15-Y-OHP
Have a 10 ton HVAC unit supporting a computer room on and military base in South Korea. Alarms are "Loss of air flow" and "Overtemperture" Sure overtemperature will ocur with no air flow.-- Filters are clean, blower drive belts and wheels are in good shape-- I think the problem is with the small pc board with the single sensor on it. "Senser Board-- Part number 0617222. Here is the problem-- this unit was made in Australia and the factory closed and went to China. Assuming this is the problem, Where can I get a new board?
This site cannot give that information to a diy'er and if you are a pro you need to get 15 posts to apply. If you are not a pro it would be best to get a service call.
Originally Posted by W Ahlberg
"War is cruelty,and you cannot refine it." Sherman to the leadership of Atlanta prior to burning the city.
Studies say Fox viewers are less informed about current affairs than people who watch mainstream news -- and even people who don't watch the news at all.
"Another means of silently lessening the inequality of property is to exempt all from taxation below a certain point, and to tax the higher portions of property in geometrical progression as they rise." --Thomas Jefferson to J. Madison, 1785.
Sounds like dirty air filters!
The alarm looks for differential across the return, which incorporates the filters and indoor fan suction.
Dirty filters would result in "Loss of Cooling" which would result giving over temperature alarm.
i would not blame the board right away
you probably have a faulty sail switch
double check it for open/close/stuck circuit