trane will do that start up factory needs their warrenty to start...check all that electrical down to the compressors and low voltage strips..if it is still they same the unit will sit because it is looking for its sensing point to look at?and a 10,000 ohm resistor on TB-4 1..2 will get it going for check out then work the panel temps setpoints.the bigger stuff is easy to start-up...Caution on that air section where the fan motors are always straddle on the fan frame when doing belts and other visuals never be 100% weight on the metal base...moisture from the evap weakens the welds and it isn't a curb supported area underneath where your pix show it.the guys on this site have the latest on the HI panel for sure.the OEMs want the sale...you install it and they get the service first year ok? but then it's yours work the panel when you do service to get familiar with it.get yourself a 3/8 chuck for your cordless drill and those panel screws and a coffee can to store them.pix are of units up on roof of Norstrom's Long Island
Originally posted by Dowadudda
Most important than anything else. Will this job come in profitable??
When the building was built it was as a supermarket. It had one big Season Four unit on it for refrigeration reclimation. The building was vacant for 3 years with no heat. The town building inspector theatened the land lord to fix the leaking roof or they were going to condemn the thing.
So last year they paid us to scrap the old Season Four unit so they could slap a roof on the place.
Normally a retail store would use 4 to 6 individual units. I inspected the ductwork and it was usable. So after all the numbers were crunched it was decided to go with one big unit.
We are supposed to get factory start up but I have to get enough info. just to get the heat running ASAP. Like by Wed.
Many Ds we should make a few buck on this. Ho Ho Ho.