Office and warehouse in both Crystal River & New Port Richey ,FL
Originally Posted by CoolIsGood
Well according to this carrier document about the 25HCC5, it doesn't seem to say anything about two stages, so it looks like I have a one stage heat pump.
I'm not interested in playing around with the wires myself. I want my contractor to come back and do it RIGHT. But, so far I have lost trust in him.
How likely is it that my coil will freeze up as my contractor says if the air handler drops the fan speed during a dehumidify cycle? Should I just go ahead and demand for him to hook up the dehumidify function of the air handler?
Not likely at all,IF the duct system is sized properly,IF not then could be.
The interesting thing is that for the thermostat I have (ecobee), they only show a wiring diagram where the Dhum is utilized under a section called "Dual Stage Furnace with Dehumidifier and Two Stage Heat Pump"
Maybe this is where the contractor got the idea that you cannot dehumidify safely with a one stage heat pump.