York warning help
I have a York chiller with a warning eroor on the screen-
What is this warning? No specifics listed that I can find?
Are you sure that's exactly what it says?
Haven't seen that error before but thats probably not suprising!
I think you will find your listed S# is the part# for your control cabinet!
Some of the Yorkies here may have seen your problem before.
I'm good at making things cold...You can ask my first two wives!
Check your press. transducers with chiller off if possible to see if one is reading out of wack. If not possible, check them with a gauge. I have seen evap. press. transducer or probe error but this warning is usually noncondensibles, making the approach negative.
Yes, exactly what is says.
Are you sure it's not reading something like "Evaporator transducer or probe error"?
Noncondensibles, most likely.
God Bless the USA
I'm with RandyS, you've got air!
When the going gets weird, the weird turn pro. HST