setting a low pressure switch. i find different techs setting differentials crazy ways.
refrigerant type 404a
find your temp you want 35f
the range you want to have cut in at 40f convert to 85psig
cut out at 30f convert to 70psig
now subtract the two pressures and there is your differential. 15psig
does this sound correct?