Did a compressor change out on lennex system yesterday. Boss tells me it is going to take #14 410a , so I did not even look at tag on unit. After I filled it (weighed it in ) started it up. Pressures 320/100 89degrees in house . 18 subcool and 35 superheat. I knew the charge was off , but could not stay at house any longer , customer had to go to work, plus it was dark out . Went back today to investigate pressures .
Today I see that it is r-22 , recovered refrigerant , triple evacuated , refilled with correct refrigerant . Pressures are good , subcool at 9 superheat at 18 pressure 210/65 with home at 73 degrees .
Am I going to have problems with this system in the future because of my stupid , dumb ass, mistake ? I still cant believe I did this . I know **** happens, Stupid is as stupid does!!