Just wanna see if anyone has some advice!
I have a couple TSC120 Packaged cooling RTU's giving me similar issues.
Heres whats going on with one unit...
OA Temp 90 Degrees
Entering Coil Temp 75 degrees
Leaving Temp 59 Degrees
Circuit 1 270/75 14 SH
Circuit 2 320/80 30 SH
Now the only reson my pressures on circuit 2 are so high, was because i wanted to add some gas and see if i could get any reaction out of my superheat. obviously not much success dont seem to have any significant drop across the drier..
According to the Service Facts with the outdoor temp and entering air temp i should def be running a lower superheat...
i mean i find circuit 1 acceptable but circuit 2 is just way out there...this didnt create a call, just came across this on an inspection