Results 1 to 13 of 77
Thread: New Zoned System Trouble
10-31-2004, 01:19 PM #29
Excess humidity causes:
1.Improper refrigerant charge.
3.Air flow too high.
4.Supply side air leakage,causes infiltration.
5.Return air leakage.
6.Building envelope problems,wet crawl space,etc..
That's all I can think of right now.Anyone else,free free to chime in!
Number 1 is possible,as well as 3,4,and 5,from what you have told us,the picyitres,and their lack of any solution to date.
Was the humidity ,high, with only 5 tons?What about the previous system,humidity wise?