Originally posted by mathias PSMURF Tech,
If you can I sure would like to get your pics of the Trane e-mailed to me, I would be using them in a class!!
My e-mail is LKelly 641@Adelphia.net * and any other Pics of that nature.
freonrick; ithink 5 were cracked. customer decided that they could get some machine shop to repair. well they did a great job of replacing the vanes but i spent almost a day
cleaning and reassembling so they would move freely
delta: i work for jci. we got lotsa techs to check stuff like that. fyi this machine is totally controlled by a dx9100
cool: this 600t still puts out about 450t even with lotsa condenser tubes plugged. metasys calulates tonnage using flow & temp measurments
weez: no plate two floats. checked both. checked liquid drain from cond., economizer etc. used one of those fiber optic snake viewers.