I would like to put this question to bed if possible. I have a carrier compressor. it has 2 elctrical unloaders on it. It also has hot gas bypass on it. The question is do i set the unloaders first. and set hot gas bypass or do i set hot gas bypass and skip unloaders. I have it set know for unloaders to come into play first, the reason for that is energy savings.Part two of my question is why would someone install both methods on one unit???