Results 14 to 15 of 15
Thread: Copeland Help
03-18-2005, 06:16 AM #14Professional Member
- Join Date
- Apr 2004
- Lubbock, Texas
CALL A PROFESSIONALOriginally posted by ssscarpone
I put the red on the high side (insulated suction line) and the blue on the low side the smaller copper tube.
And two other businesses said the same thing.
ssscarpone does not even know high and lowLearning never ends and everyone has something to teach. Some people teach me what to be like others teach me what not to be like!
03-18-2005, 06:42 PM #15
low side 150 high side 130 bad valves
i have seen a lot of bad valves and low side higher then high side maybe i missed class that day but never seen that
is it a heat pump in heat mode and your connecting to suction line and liquid line instead of suction port of compressor. on a lenox unit it is tucked up above the line set about 8 inches or on the compresser suction side about 6 inches from the compressor. i could see 110 low and 150 high if valves are gone totaly you would be equal or at least close. check you gages are the needles on 0
make sure they are not bipassing and talk to you instuctor
maybe he will make it a class efford. i know i would
if it is the compressor call lenox and get the right one for the unit also get the cap for it to. always change the cap and start capif one on any compressor or motor replacement