can someone help me with this Lennox no# data plate unreadable
AHH254 ip/ru 8
gf06 69 110385ah28113v this is off the compressor
Hs61-211-1ff this was on inside panel
talked to lennox they thought compressor was 2.25 ton
but the no# on the panel seems to be 1.5 ton which would
make more sence with 1/4inch and 5/8inch line set. our
salesman sold a 80,000btu furnace with 2.5 ton coil and
kept condenser it has been running this way since Jan
thanks in advance
HS6-211 would be a 1.5 ton from the 1960s.
The liquid line is the metering device. If some maroon put a new coil in and left the meter in place, it has 2 restrictions. Wonder how it is even working!
It should be removed and a matching outdoor unit with new lineset installed!
Thats what i thought we replaced the 1/4 in with 3/8in had to change the piston about 5 times before we found a good balance thanks for confirming.