I've got a problem with an evap coil. Expansion valve went bad, took out the compressor. Replaced both, installed new drier, now the coil will frost up in a matter of 12 hours. This is a walk in cooler, roof top self contained unit, R-22. Head pressure 225, suction pressure 50 lbs. box temp 43 degrees. What things should i check out?