I went back over there this morning to see if there was a siliniod I missed (no). I ck the amps again 4.5 on one 6.5 on the other one. ck volts again all the phases were good. Just looked at it for about 5 min and my phone started to ring, it was YORK telling me the compressers came in. I hoped in the van to go get the and started going at it. After removeing the r22 from the system I opened the system and and blew through the lines to see if the drier was cloged before replaceing it (it had no trouble going through). I removed the compressers and put the new ones in , replaced the drier , Pressure tested , pulled a vacume and waighed in the charge and they started up GREAT! That was the problem bad valves in both compressers. I am makeing it sound easyer then it is. I had to call anouther guy out there to help me lift those .......... up on the roof. They were both already piped togeather mounted on plywood , and about 7 hours later they just started right up. It could have been worst my psi could have not moved and it could have been 95 outside or raining. I still do not know what caused the compressers to fail like that. I have not been with company long and so many people have worked on it in the past every safty was bypassed. I am going to go back and install a low ambiant and low psi switch. Thanks for all your help guys.
ps sorry about my spelling , but that is OK