ok thank you everybody who gave me advise! I found the problem it was going off on CLO. I jumpered and the contactors sucked in put my gauges on and wow high pressure. The hvac tech before me must have charged it beer can cold. I recoverd some refrig and put the correct charge on it. Now it runs fine. The unit conditions a kitchen and there is alot of heat load which may have been why the guy charged it like he did who knows. Being new to the facility I was told to only reset it and not givin the chance to take any time with it. Again thank you everybody you made me look good to the boss! Sorry I didnt post sooner. I had a major problem with a very big York chiller. I got it running seems something wasnt right in the programing. I am clueless on that unit but it's running. Good thing I have you guys as back up lol.