Hi Got my feeler hurt on this one. Got a call ice machine low on ice beeping 3 time interv. Sent my newly hired grocery store tech out on it. He called cant find problem. I thought I'll show you how its done. Man was I wrong. I check for leaky water sol, blew out cond, unplugged cond fan went up to 375psi, unplugged liquid sol and bypass sol pulled into vac, pulled out charge & recharged with fresh 22 to factory spec. It takes 60 min to make a batch, harvest near norm. Here are the vitals @ 5min into freeze
Suction 61psi should be 38
high 205psi should be 245
suction lines at evap 26º
both side of hot gas valve 82º
compressor pulling 7amp.
Call factory tech talked to at least 3 of them they were no help.
I told store manager he had a weak compressor. I found out later he call mister Big out to fix it he didnt.
Got any ideas Its prob something so simple easy overlooked. Thanks