Originally posted by frozensolid Sounds like your not forcing you EPR open.
Your right. Once I got it diagnosed and the part in hand, the service manager paid me a visit and went up to the rack and told me I could have by passed the EPR by either switching the controller to low temp, from med temp. Also I could have screwed the stem in on the EPR itself.
Originally posted by condenseddave Lift the hood and look.
Shouldnt take tooooo many more "under the hood" inspections to realise where they put certain items on these cases.
If it was me taking some guy on who wasnt up to speed on market work and SUMMER WAS APPROACHING FAST .... I might consider taking pictures of all the variables... then pointing out where the goodies are hidden.
But that would be too easy.
And since I'm teachable and have some knowledge ... I should be able to simply ask the right questions and get all the answers I need in short order anyway.