Just to keep folks posted - Loytec found a couple of problems and will correct then in veriosn 4.xx.
We're still working with Loytec on new issues found.
Regarding the Red Lion panels. I spoke with their tech support and they do not support cross subnet communications. They do have a panel with two ethernet connections that could talk to two different subnets.
Apart from this the panels are great.
Is anybody aware of the "DPAL BACnet, error" on a ME-215 deivce. I am not able to scan any network device or object. the error lodg shows following error message-
Could not configure BACnet interface (DPAL error 200)!
LGTW: Fatal Error: Could not start DPAL BACnet, error 39!
Could not start BACnet DPAL (lgtw)!
BACnet/IP? Put in a gateway address.
What's the end result of this situation? Has anyone use these screens on more than 30 devices? Does anyone find them polling for master well past the master?
I am using this on the MSTP bus, but will try and and put a contemporary controls router and convert to IP and see what happens. What has everyone else's experience been with these and BAcnet MSTP?