filter dryer blew desiccant through r- 404 system. Took out headmaster and and txv! How do you make sure desiccant is out of the system? the refer rack is on the fourth floor the evap on the first.
what caused this? how to prevent this? hows the best way to clean up the system?yes its cold in Michigan. 8x8 box, single evap cooler.