Unico AHU H/P Match up
Ran into a a Unico ahu model # MC2430CX yesterday, that had a Rheem
UPNL 024 JAZ 410A Heat Pump attached to it. The Rheem unit is toast. Flooded by water. Trying to find a hp match for the Unico AHU.
But I don't think Unico pays for testing to get listed on ARI, do they?
What do you usually match with these Unicos? This on is an 06 and has dual refrigerant capability. I'm sure it will need a txv.
I'll put a call into Unico tomorrow morning but with the ASHRAE show going on, not sure what response I will get.
Unico has matches on AHRI.
Those HV air handlers zap efficiency but they have a loophole to be sold.
Armstrong/Air Ease 4SHP14LE124 11.00 SEER
Carrier 25HPA524A30 11.20 SEER
ICP N4H430A(G)KB 11.00 SEER
Lennox 14HPX-030-230 11.00 SEER
Nordyne FT4BD-024K 11.00 SEER
Trane 4TWR4024C1 or 15i 11.00 SEER
Did they get that loop hole(Constraint space) extended. Or does it only expire this year Balie.
Ahh I see it now...I missed it. Just got to figure out what the other stuff listed in the indoor section is A00808 or something , looks like a txv.
I knew the efficiency would stink.