Some times you gotta put em where the customer wants. Other than the the concentric pipe sticking out too far. Have put them in like that cause the customer doesn't want a hole in his roof and have water leaking issues.
In another pic I see the flex is pinched, that's not good. Other than I'd want to see where the condensate pump is draining to, and the furnace condensate drain is double trapped. and the number one reason is never put a 90% furnace in an unconditioned space. Water, below freezing temp. hummmm
Last edited by bribone; 01-20-2010 at 01:03 AM.
Reason: saw something else