I have all the logic written in the mP580 for static reset just need to feed the maximum damper position from the boxes to network input on 580 which is percent snvt. Since Trane does not really give you a damper position so to speak I am having an issue. The vav damper position is hidden inside the unitStatus output as cool output. How do I connect these up to a max block in the wire sheet? I am very new to AX and have no formal training so for some of you this may seem easy but not able to figure out how to separate that cool output so it will bind with a max block.