Boilerman workin' on geo
I have a Bosch 5 ton water to air, tripped on freeze stat. Reset it, some #
gpm=15 air split=18 water split=6.9
suction=74psi ( r~419 ) superheat=12 flow center circs 1.3 amps
wtr in=35.9 wtr out=29
Boilers... I'm good... geo's I have lots to learn
Any input appreciated
I gotta feeling I'll be back
I may not be the sharpest knife in the drawer, but compared to some I'm a razor...
What kind of loop system does it have? Open loop, closed horizontal, closed vertical, or pond loop? Is the freeze stat reading actual water temps, or is it based off of the freon pressures? I would also want to know what percentage of antifreeze is in the water.
It is a closed loop, non pressurized flow cntr. The flow cntr. was clear, but smelled heavy of methenol?
Originally Posted by hoytmania
Slinky piping horizontally. The sensor is attached to coaxial