Results 1 to 10 of 10
Thread: Bad motor install
12-20-2009, 01:30 PM #1
Bad motor install
Hummm. Something tells me you didn't get the right motor...
12-20-2009, 04:41 PM #2
hmmm..that pulley looks odd
12-20-2009, 07:17 PM #3
Is the driven pulley on the blower healthy? It may be the angle of the shot but it looks like there's no channel for the belt to ride in, like the inner wall has been warn off???If YOU want change, YOU have to first change.
If you are waiting for the 'other guy' to change first, just remember, you're the 'other guy's' other guy. To continue to expect real change when you keep acting the same way as always, is folly. Won't happen. Real change will only happen when a majority of the people change the way they vote!
12-22-2009, 01:19 PM #4
Pulley is same diameter as the motor itself! And look at the diameter of the shaft hole. That pulley was taken from a much larger motor.
They sent a boy to do a man's job.
12-22-2009, 05:01 PM #5
looks like a "speed me up" Carrier!
12-22-2009, 07:35 PM #6
Those take OEM motors. It's a 56 Frame ridgid mount but the shell and stator are backwards. So far, you can only get them from Carrier. They also have an internal overload with external wiring for the control circuit. Our cost is about $320.00 for a 3/4 HP 230V 3PH.R2B4BTU
12-22-2009, 09:47 PM #7
not to mention the half arse controls install.Build it and it will break. Fix it and it will work. Ignore it and will cost more. Patch it and it will get worse. Cross the bridge before the flood.
01-01-2010, 10:34 PM #8Regular Guest
- Join Date
- Jan 2010
- Levittown, PA
Wrong replacement motor. Shaft is too short.
01-01-2010, 10:39 PM #9
01-02-2010, 09:33 AM #10