Does anyone know whether or not the HPCO has a shrader under it on a YCAL?
Isn't there an ASHRAE standard or rule that states there can't be any shut off device on an HPCO? And I think it includes schraders too. Most (if not all) of the recips and screws I've worked on haven't had one unless someone added one. And usually it's a flare fitting that you can't put a core in anyway. I'd be very careful and at least isolate the discharge line and get the pressure down a little.
Low Pressure Forever!
If you know heavy metal, you can work anywhere-Dave Andreson
Anchors Aweigh my boys, Anchors Aweigh!
Farewell to foreign shores, We sail at break of day. Through our last night on shore, Drink to the foam. Until we meet once more. Here's wishing you a happy voyage home!
The switch that he is refering to is barrel style with a depressor inside of it female flare to male flare upon removal of the switch you will lose a small amount of freon if your quick but that it other wise there is no other way to replace unless you take all the freon out there is no other way to isolate to replace.
Arguing with your Boss is like wrestling with a pig in
After a while you realize that while you are getting
dirty, the pig is actually enjoying it.
It is not exactly cheating, I prefer to consider it
creative problem solving.
25 years ago we had Bob Hope , Steve Jobs , and Johnny Cash today we have no Hope no Jobs and no Cash !
I can fix broke but i can't fix stupid !