Why shouldn't it work?
[Edited by Boss on 12-29-2003 at 02:24 PM]
Looks like a good trap to me. What's the problem again??
Thanks Frank I busted a gut looking at that!Too funny!
Take your time & do it right!
Looks like the installer didn't want to put in a shorter B-Vent in, so he just put the dip in! Or... He didn't want water to get back into the heat exchanger if the cap came off outside. :-)
Trap looks a little rusty too. And, is it touching the insulation below it? Nice wire run too.
What is wrong with those guys its almost like their trying to do a bad job!
Might as well add a drip leg to that thing! HA!
Originally posted by MikeJ
Nice wire run too.
It's called a thermal limit control.