We had an old York Chiller pulled and a Trane RTAA installed. First two days we ran on 100% outside air, and were able to get by. Start-up day the temperature steadly climbed, they had to trace down a few glitches, finally they were ready to start. I turned on the pumps, and put the AHU valves to auto. Another problem came up with loose sensor wiring. Watched the water temp. soar to 86 F. Finally they started the machine, waited till the water temp. hit 70s, put O.A. Dampers in auto. When temp. was down to 50s, went into the building and told them to close windows. Should have seen the look on their faces, thinking they were going home. One lady crossly said bosses are going around checking temperatures, highest was 78F, found them, told them to hold off, we had cooling.
Employees looked like they wanted to string me up Still have my record of no closed buildings due to temperature.
Chiller pulled temperature down before Start-up Tech. could get all the readings.