1. Regular Guest
Join Date
Jan 2009
Posts
46
Post Likes

## Math Quiz

If my home losses 80000 BTUh, and I live in a region with 3784 Heating Degree Days, then I use 7,265,280,000 BTU per year.
(BTUh x 3784 x 24)

Which is 72652.8 Therms per year.
(BTU / 100000)

If I pay 113 cents per Therm, then my base cost without factoring AFUE is: \$8209.77 per year.
(Cents per Therm x Therms per year / 1000)

This figure seems pretty high to me.

2. Regular Guest
Join Date
Feb 2007
Posts
1,002
Post Likes
Originally Posted by unclebingo

If my home losses 80000 BTUh, and I live in a region with 3784 Heating Degree Days, then I use 7,265,280,000 BTU per year.
(BTUh x 3784 x 24)
If you lost 80,000 BTUH every day for a year, you would only lose 700,800,000 BTUH (80,000 BTUH x 24 x 365). Are you at one of the poles?

The figure (80,000) is what you house needs (at design temperature); so you will need to burn more gas to yield that quantity. Sorry.

Perhaps one of the PROs has a formula for approximating usage based on HDDs.

Amp
Last edited by ampulman; 09-13-2009 at 04:33 PM. Reason: formatting

3. I use bin data. HDD's is too misleading.

When its 64° for 24 hours, you will have had 1 HDD. Your not going to loss 80,000BTUs in 24 hours at 64° outdoor temp.

4. Regular Guest
Join Date
Nov 2008
Posts
1,673
Post Likes
Originally Posted by unclebingo
If my home losses 80000 BTUh,
at what inside/outside temp, averaged over 24 hours?

5. Regular Guest
Join Date
Jan 2009
Posts
46
Post Likes
I've yet to collect the HDD figures, and for the purpose of building the formula I was using default figures from www.hvacopcost.com for both HDD and BTUH loss.

When I can gain access to the house I plan to perform a full Manual J to calculate the BTUH loss, and I'll calculate HDD per "beenthere's" post, i.e.

Base Temp 65f
Monthly 1% DBf
Jan - 54 - 31 days - 341 HDD

I'll only use monthly 1% DB averages so it's going to be an approximation.

If I understand you guys correctly if (subject to ManJ) the furnace has to make up a 80,000 BTUH loss to maintain 70f inside, which totals 700,800,000 BTUH per year. (80,000 x 24 x 365). And wikipedia's formula to calculate annual kWh is correct, i.e.

Area x U-value x HDD x 24/1000

Then do I just multiply the yearly BTUH loss of 700,800,000 (Area x U-value) by the number of HDD's by 24 / 1000 = yearly kWh used

Then I calc my cost per kWh?

6. The furnace only has to make up 80,000BTUs when the outdoor temp is at design.
Which probably is only a few hours/days a year.

When its 54 outside(11 HDD), it may only have to make up 13,538 BTUs an hour.
But, even that is not a true statement. HDD does not take into account, solar gain. So at night time, it might loose 13,538 BTUs an hour, but during the day with the sun out. It might only loose 8,000BTUs an hour.

7. heat loss times times degree days divided by (indoor design temp-outdoor design temp) x a correction factor, divided by system efficiency

8. Regular Guest
Join Date
Jan 2009
Posts
46
Post Likes
Originally Posted by Carnak
heat loss times times degree days divided by (indoor design temp-outdoor design temp) x a correction factor, divided by system efficiency
If I'm using monthly 1% DB data then outdoor design temp varies from month to month. Does this suggest I need to calc each month?

What is the correction factor?

9. you use the design temperature difference, usually for a house the 97.5%

the correction factor compensates, depends on your area.

10. Regular Guest
Join Date
Jan 2009
Posts
46
Post Likes
So the correction factor is only needed if I adopt a standard 97.5% design temp difference?

I know that the Manual J spreadsheet I have automatically calc's the HTD for me when I enter the climate data. Does that mean I can omit the correction factor from the formula?

11. no

The correction factor is sort of like an average of how long the furnace runs per hour over the entire heating system, if the furnace was sized spot on to the design heat loss

So in a deep freeze it runs steady, maybe in mild winter weather it runs 10 minutes per hour

It depends on where you live. Same lattitude you could be in the mountains, on the coast , maybe in the prairies, the geography plays a part

you have to pony up and say where you live

12. Regular Guest
Join Date
Jan 2009
Posts
46
Post Likes
Cedar Rapids, Iowa

But understanding the formula is more important to me than just getting you guys to tell me the answer.... I wanna learn!

13. Regular Guest
Join Date
Feb 2007
Posts
1,002
Post Likes
You can get an accurate figure for HDDs and other info at:

http://www.wunderground.com/history/...omHistory.html

Amp

Page 1 of 2 12 Last

#### Posting Permissions

• You may not post new threads
• You may not post replies
• You may not post attachments
• You may not edit your posts
•

## Related Forums

The place where Electrical professionals meet.