service call was unit not cool, (but the house is cool not enough but it is cool), unit runs all day and night, never turns off.
set gauges low of r22, cut coil and washed coil, coil dirty.
soldered coil back to unit, opened valves done, so i thought got a call back still doing the same thing.
temp-118 liquid line temp @ evap coil-27.5
suctionline temp-73 (6-8 from compressor).
any ideas guys really need the help thanks.