I think it was an 8",,, I went up to investigate after having no superheat on a 3 ton Payne. The original no cooling problem was from a bad contactor.
There were 2 systems in the attic with small returns. Customer said they were operating fine like that. I probably irritated them by taking pictures and just my overall unbelief that things like this are done by "contractors",,,,, oh well.