electrician has not been there for weeks..installers paperwork said 11"..so they say, i did not read them.
Guide says 12" from wall, code says 30" at access, guide says unrestricted on other remainig sides(2x). Most will do 24" which is what it looks like your guys did on the outside units. The furnaces by code are supposed to have 12" added to thier dimensions for min. clearance. That is some really clean work. Im guessing that the furnaces all share a common return?
Some Talk, Some Do
"I'm just proud to be here."
Trace Adkins Blog Web Facebook
correct...with the common return. the original was a lennox monster. One unit and dampers for temp control...never did work right we where told. Now the south facing units can be cooling wile the north ones are heating
Very nice! Refrigeration piping sure looks nice. Just curious, how many manhours total?
not sur on total man hours...people get pulled off jobs to do other small projects and such. we have been there for at least a month i think. my only part has been control wiring for smokies and will go back for start up after electrician is done