I thought it sounded like the condensation was after the drain, in the supply plenum.
As stated high static can lower cfm's to create the moisture/water out of the ducting close to the plenum.
Another thing to have the contractor check is the p-trap if the evap. coil is on the negative side of the blower. May be no trap or open clean out uphill of the trap.