Have a call on a split system - has a 15 ton new american standard condenser duel compressor. is piped to a rheem 12.5 ton slab coil with duel expansion valves. valves are 8 ton each on a 12.5 ton coil. the weird part is the sight glass will not clear up no matter how much refrigerant is added. right now the there id 70# suction and 300# head while only running on 1st stage compressor if i energise the 2nd compressor site glass is still foaming anf head goes to 365#. I would think the coil would be flooded and not starved.