Liebert control Ideas
I have a Liebert Mini mate 2 that I would like to monitor. I am looking for something that will alarm if there is an issue with temp, humidity, or power failure. I would like to be able for this system to send an email, text, or phone call if there is an issue with this unit. Just wondering if anyone here can recommended something.
Take a look at MAMAC's IP controller:
"Open is as open does."
- Forrest Gump
"Can't we all just get a Lon?"
- Garry Jack
"BACnet: integration or interrogation?"
- The Janitor
"Open protocols? You can't handle open protocols!"
- Nathan R. Jessup
“What’s that? Aaa… open protocols? Don’t talk about…. open protocols? Are you kidding me? Open protocols? I just hope we can hardwire an interface!”
- Jim Mora http://www.youtube.com/watch?v=U7fjDS0jKiE
There is a factory ISWEB option that can do those things except the email portion, which is incoming in some future firmware update "soon"TM.
You need the 485/Web Network Card from Liebert. You can put it on your company network and assign an I.P to it for you to view each unit. It will send you email with Alarm notifications. I have installed many and they work great. Hook right in to the unit and you can pull the I.P and see what the unit is doing at any time with full web page display.
Thanks for the ideas. Looking around I found a stand alone unit from Avtech (Room Alert 4E). It dosn't hook directly to the unit but, is able to monitor a number of different room conditions. I connects to the internet & phone and if there is a reason for alarm it can email, text, or place a phone call. I spoke with a rep and it sounds like this may work for my particular application. Has anyone else here used this product or something similar?
Can it take dry contacts? If so you could put a contact board in the AC and know about a problem before the room gets too hot.
Old thread but are the monitoring options the same?
I have a MMD12E7PREOD I would like to monitor and have some control via Modbus, seems to be the same card as the DS and System 3 units?
"How it can be considered "Open" is beyond me. Calling it "voyeur-ed" would be more accurate." pka LeroyMac, SkyIsBlue, fka Freddy-B, Mongo, IndyBlue
BIG Government = More Dependents
"Any 'standard' would be great if it didn't get bastardised by corporate self interest." MatrixTransform
- not my website.
Versatile Hunting Dog Federation - www.vhdf.org/
Minimate 2 units have web cards you can put in as well. Almost the same on the monitoring side as the advanced micro units.
Harris Integrated Solutions
Formerly Liebert (Emerson Network Power)
Expressed opinions are my own