First welcome, second please re-read site rules (DIY),
That said, it sounds like the condenser and the fan are connected together somehow. What needs to happen is that the "G" terminal need to start the fan. Someone likely didn't install an isolation relay to separate the cooling signal and the fan signal.
try < We don't give recomendations for DY sites> if you need specific advice on how to do so.
Last edited by beenthere; 04-23-2009 at 07:25 PM.
Reason: Removed DIY site name
If sense were so common everyone would have it !
All opinions expressed are my own. Any advice provided is based on personal experience, generally accepted fact or publicly available information. As such, it is worth exactly what you paid for it, not a penny more not a penny less !!