Hey Bret. SMOOCHIES!!!
BOB Start kickin some a$$!!! Get ornry! Get mad.... payback time... then calm down and get your butt in here!
Double SMOOCHIES for you!
Hey Gang..... only 3 calls today! and its 8pm and I dont HAVE to go out anymore today!
one call was.... ground floor freezing! Set on 75 and was 70.... damper wasnt working. Stuck..... loosened it up.... will order a new one.
Another call.... lower level not cooling..... only 8v on R. opened up ahu and found floats wired through R. Rewired through Y.... no 24 on Y.... condensate pump float open.... found breaker in panel marked upstairs bath - off. Turned it on and entertainment center on ground floor came on. Condensate ump came on and a lebleu water tank pump started up.... and ran and ran and ran.... (it was empty) unplugged the pump and all was well! I am sure someone shut the breaker off to kill the water tank.
First call was easy at an urgent care clinic.... bad dual capacitor.
Having a bonfire tonight.... SMORES..... yum