Originally Posted by JonDeere
that electronic filter not on a seperate fuse?
wiring comes from unit to filter assembly via cord that can by unpluged and assembly has an off switch. It was install with system, so any extra draw was a known fact at time of installation.
Your going to have to get your electrician to pull new wire no way around and if your going to do it i would consider running #6 wire w/50 amp breaker and be done with it...
Originally Posted by ASNNY
We don't do a lot of electric heat up here in the Northeast. However, we do a fair amount in Cottages here in the 1000 Islands.
Are you near Black Lake?
Colorado's premier Green Mechanical Contractor!
Support Our Troops!
Gas is usually cheaper than electric if you run your backup quite a bit. 50amp breaker requires #6 wire for a max 105 foot run, assuming single phase 240 Volts.