Duct was not connected to electronic filter cabinet. Like the new style electronic filter?
Insulation pulled out of the cabinet. Look at the mold!
Picture snapped right before the internal relief went off in the scroll.
3 year old Carrier
38YCC048 matched to FA4ANF060
7/8" x 5/16" line set [50']
400+ psig after stone cold start and 2 minutes of operation.[heat mode]
 6 x 14 return grills pulled through wall cavities
Maximum test static .67" wc. Actual static .78" wc. and pulsating
Aluminum wire [no disconnect]
15 kW strip heater [only 10 kW connected]
Condenser "pigtail" not connected [insulation of wiring rubbing cabinet]
Duct not sealed
The list goes on
Where does this stop? This was done by one of the largest contractors in the area. Bigger is better, Right!?
[Edited by Boss on 12-28-2003 at 09:59 PM]