ICE-Con burner setup questions...
An En Mar model HTDM mua unit.
I've got this Canadian made gas fired make-up air unit with a modulating burner. The combustion fan motor is speed controlled, along with the main gas valve (2-10vdc) from a version two ICE-con board.
We replaced the heat exchanger and now the burner rumbles a bit in the middle of the modulation. Apparently version 1.7b of the software can be use to set the 6 steps in the burner operation. Each step burns hotter, air and gas are increased, the fan RPM ramps up too. Each step is tested with a combustion analyser to assure good burning. This is the procedure for fine-tuning the burner.
My question is:
The software sets up gas and RPM but the fan speed can't be dialed in with the RPM desired, only a factor number like 42.3 and so on is changed. The board then changes that to an RPM.
I started this on Friday and found the process tedious and frustrating, all trial and error.
Anyone out there done this before, with success? on this setup?
Last edited by D'Laine; 02-14-2009 at 09:54 AM.
Reason: update details