I work for a local gas company. I went to a job and the customer was complaining that her gas stove was "Torching" sounded like a blow torch. Yup they were. Well I did my checks and found instead of 7" house pressure, I found the house gas pressure @ 3+ psi. Well I did some investigating and found this outside. The water spigot next to the meter has been dripping water for awhile. Here is the picture of it. To make this even more ironic the Mrs. is a local volunteer Firefighter.