Results 1 to 13 of 20
11-13-2008, 05:43 PM #1
I love it when other companies keep me busy.
I took these few images from a no heat I ran this morning. The breaker would trip when the furnace came on. Gee, I wonder why...
This furnace's amp draw is 15 amps. Here we have a sump pump plugged into the same receptical as well as other household appliances. I think we exceeded our load here. There also used to be a heat pump here. Why the installing company did not modify this disconnect is beyond me. Putting in a single pole breaker at the main panel and running new wire from the disconnect to the furnace must have been too hard for them.
While we're at it, how am I supposed to get a pipe wrench in there to loosen the union? Don't they know the union is supposed to be outside the unit? I also love how they glued in the air intake at the collector box.
The black duct tape around this gaggle-frack of t-stat wire is so precious.
nagakatta yo mou sukoshi de atatakai hizashi abireru, honto wa gutto koraete'ta jibun ni dake wa makenai you ni, nagakatta yo mou sukoshi de atatakai hizashi abireru, hanarete sugoshiita jikan ga samishiku nakatta to ittara uso ni naru...
Not as lean, not as mean, but I'm still a hardcore, ass-kicking, hard charging Marine! Oohrah!