Our facility currently operates 8 Trane Intellipaks with Tracer Summit control software and are having problems with the ecomomizers opening up to far during the transition from natural outside cooling to mechanical. I thought was to restrict the limit the amount of outside air drawn in by reducing its maximum position on the economizer. Does anyone here know where this can be set in the software?
We are also having problems with comms from the computer to the VAVs and FTUs which periodically drop and need to be reset to restore communications. We have looked at all the suspected units and cannot find a permenant solution. Any suggestions??