Vykon Jace200 and Honeywell XL15C
I was wondering if anyone else had a similar problem!
I can't get and point values from the XL15C, I discovered all the points but all I get is nan (not a number) on my analog inputs ? All I have on the network currently is 2 XL15C and an Xl10 R/T controller. I seem to getting point info fine from the XL10.
Any advice ALWAYS greatly appreciated!
Have you tried re-writing your xl-15c program using the workbenchs' wire sheet? That's what I ended up doing with my xl-15c's. The learn function doesn't seem to work very well with the 15c. For me all of the network bindings I had in Lonspec were lost. I'll never use Lonspec for an xl-15c w/jace again.
Last edited by rad1; 10-29-2008 at 08:11 PM.