High Static Pressure on AMANA System
My neighbor heard me talk about all the changes that were done to my
HVAC system and asked me what I thought of his. He has a basement furnace/coil unit in a 2400 sq.ft 2 story home in NJ with an outside condenser. We checked his negative static pressure in the blower bay and it was 0.83 with the "fan only" on. We pulled out his 20x25 1" Flanders merv 8 filter and the static dropped to 0.43.......with the 1 inch filter slot wide open. I did not have my drill and there were no factory holes so we did not check the positive static (before the coil). The system is ~ 7 years old and he indicates it works fine to heat and cool the house (although his family may disagree). I told him I would post his model numbers to get some feedback on his system. We know it is 80% but thats about it.
1. Does anyone fimilar with amana systems know if it is a variable speed. I ask because I am under the impression that high static on a variable speed can shorten the motor life.
2. Is the system matched?
Here is the data: Amana
In the land of the blind.....the man with one eye is king....