Will my install be correct?
Customer is adding 4 feet to his WI cooler.I have done my calculations and here is what I came up with.
I figure with this new condensing unit and existing evap,I will have a 36f box @ 25f sst-with about a 11td.Does this sound correct or am I out to lunch?
- new box size:6.5x12x7-approx 80sf-average use-btuh load with quick selection guide=6954 btuh
- condensing unit(new)25f sst-7180 btuh
Last edited by cretan; 10-03-2008 at 01:07 AM.
Artificial Intelligence is no match for Natural Stupidity