We are an air conditioning contractor and a good customer of ours had the evap, lines, & condensing stolen off the walk in.
I have very little experience with refrigeration.
-6x8x8 room outside in south florida
-use for beer and produce
-looks pretty old
I was looking at the heatcraft quick guide.
It says for avg use 5417 btuh or 7274 for heavy use.
Does that sound right for a old cooler in 90-95* ambient temps?
I would like to stick with R22 since we are familiar with it.
Tecumseh has a line of r22 med temp outdoor condensing unit that will do from 4880 btuh-8890 @ a 25* evap.
Would this be a good unit for the application?
Thanks for your help.
The best thing you do is to contact the manufacturer , by giving the model no and serial no of the walkin cooler, they will select the right units for this applications with-out modefication.